Clipsal Iconic Essence Dolly Rocker - Arctic White - E40AR-AW
- 5 $4.29 $3.90
|EAN / Barcode||9311554800734|
Customisable and future-ready
Iconic is based around a unique, electrically safe grid plate, with a choice of three different skin designs that simply clip on top.
Once the grids have been installed by an electrician, it’s safe for anyone to change the skins at any time. Simply clip off the standard skins and clip on the new design.
Interchangeable standard, Styl and Essence skins provide great options to customise to suit specific decor and lifestyle.
There is no direct alternative to the clear 250ml jointing cement in the squeeze bottle. We only offer our range of four sizes with a brush incorporated in the lid. For further information please visit https://www.clipsal.com/Trade/search-results?q=jointing%20cement.
Issue When connection to EM4xxx meters using the EM4800 configuration tool, an error message pops up: "Couldn't determine unit type based on ModelNum xxxxxxxx-xx-xx" Product Line EM4xxx series meters Environment Meter configuration Resolution Un-install the current version of EM4800 Configuration Tool that you have installed and re-install the latest version of the tool. Latest version of the tool from the following link: EM4800 Configuration Tool (SEMetershop V184.108.40.2064) This config tool supports the new Demand feature released with meter firmware revision 1.46 * IMPORTANT NOTICE: This version is NOT measurement Canada Approved.
Issue: Configuration of SRC battery packs via the LCD display Product Line: Smart-UPS Online Environment: All SRC models, All Serial Numbers Cause: Batteries need to be manually added to the UPS in order for the unit to properly calculate runtime Resolution: Procedure for Configuring the number of battery strings through the display interface or LCD menus: 1. Press the Enter key to select the main menu. 2. Scroll down to configuration. 3. Press the enter key to select configuration. 4. Scroll down to battery setup by number of battery pack. 5. Enter the correct number of attached battery packs. In order to setup the external battery packs, please key in as (Ah of battery) x (total number of batteries). Example 1: If there are 16pcs of 5Ah battery in series (for 5kVA), the total Ah number is 5Ahx16pcs=80Ah. Example 2: If there are 16 pcs of 100 AH batteries in series(for 5 KVA), the total AH number is 100 AH x 16 pcs=1600 AH Example 3: If there are 2 strings of 16pcs of 5Ah battery in series (for 5kVA), the total Ah number is 5Ahx16pcsx2 strings=160Ah. The 80Ah inside the table is the default setting for 5kVA/6kVA (1 EXB: 16pcs of 5Ah battery) The default setting for 8kVA is 140Ah (1 EXB: 20pcs of 7Ah battery) The default setting for 10kVA is 180Ah (1 EXB: 20pcs of 9Ah battery). If “Ext total battery Ah” is set as 0, it means there is no external battery connected. "